- Video Introduction of the New Aztec AMC Evaporative Cooling Air Turnover System
- Designing Data Centers as Thermos Bottles
- A New Video on YouTube Describing How the Aztec Evap System Works
- Aztec To Be In Capacity North America Exhibit Hall
- Virtual Reality
- A Simple Concept That Saves Big Dollars
- Indirect Evaporative Cooling Research Project Launched
- Canadian Patent Granted for Mestex Digital High Turndown Burner
- So You Think Your Critical HVAC System Is Reliable?
- Aztec Provides Fresh Air Intake Penthouses for Data Centers in Northwestern US
- Shading and Make-Up for Building Designers
- Credibility and Trust
- How I Spent My Summer Vacation
- Too Hot to Handle? A Simple Reminder.
- Preaching to the Choir
- Aztec Indirect Evaporative Cooling System on Display at DFW ASHRAE Golf Outing
- How We Used To Do It
- Air Pollution and HVAC
- Mestex, Division of Mestek YouTube Channel
- Aztec Evaporative Cooling for Data Centers at Data Center World
- GreenBuild Toronto
- Trane Division of Ingersoll-Rand in Lawsuit Over Wireless Technologies
- New BIM Objects From The Aztec Brand
- DOE Proposes Building Rating System
- The Importance of Correct Static Pressure for Direct Fired Make-Up Air Equipment
- Instant Online Document Lookup Using Microsoft Tags
- Do Evaporative Cooling Systems Use Too Much Water?
- Sustainability at Mestek Dallas
- Facebook Offers Their Outside Air Cooling Solution To All Data Center Owners
- Restaurant Energy Saving Idea That Can Be Used Anywhere
- Planning for Volatility
- Ever Wonder Where the Power Goes in a Data Center?
- ASHRAE TC 9.9 Expands Data Center Temperature Ranges Again
- Green Buildings Get Another Boost
- ASHRAE Show Report
- The Story of SHR or Why My Classroom is Stuffy
- CFD, Air Turnover, and the Pharmaceutical Industry
- It is not sustainable if it is not maintainable... or if it breaks down
- Accounting Rule Change Might Impact HVAC
- Reduce electrical demand load with an Aztec indirect evaporative cooling unit
- Lower Cost of Ownership with the Applied Air FAP
- Everything You Want to Know in a Flash
- Data Centers and Evaporative Cooling Webinar August 23
- New "Green" Product Announcement
- DDC Application Case Studies
- PowerPoint showing the importance of gas pressure, static pressure, and voltage
- Webinar: 'The Importance of Correct Gas Pressure, E.S.P. and Voltage'
- An Old Solution to a New Problem
Evaporative Cooling Anaysis for Data Modules in Two Diverse Climates
One of the common concerns expressed about the use of evaporative cooling for data centers, server rooms, telecom facilities, or other facilities housing heat producing electronics is the ability of evaporative cooling to achieve the target inlet conditions for the electronics.
These two psychrometric charts show the results of an actual analysis in two distinctly different climates. The target server inlet temperatures were between 65 and 85 degrees F and between 20% and 80% RH. The mechanical system criteria mandated that direct evaporative cooling be used.
The proposed mechanical system consisted of a direct evaporative cooling system with 12" cellulose media, a steam humidifier, DDC controls, and a hot aisle/outside air mixing section. The controls would be configured to modulate the outside air dampers, hot aisle dampers, evap media water flow, and the humidifier to maintain the target conditions.
Server Inlet Temperatures from Evaporative Cooling System in Pacific Northwest US
Server Inlet Temperatures from Evaporative Cooling System in Southeastern US
As you can see from the charts the proposed system would easily achieve the desired results. In fact, it was found that outside air cooling could achieve the targets during roughly 15% of the year, direct evaporative cooling could achieve the results during roughly 60% of the year, and remaining hours of the year when the air was too cold to properly operate the evaporative cooling without fear of freezing a combination of hot aisle and outside air supplemented with the humidifier would hit the target. The only excursions of temperature over the maximum target of 85 degrees would occur for no more than 5 hours a year based on the NOAA TMY2 weather history.
While not every location would achieve these results the diversity of climate for these two studies imply that direct evaporative cooling, with creative use of mixing and controls, will work in many more climates than most people expect. To further expand the capabilities of evaporative cooling an indirect evaporative cooling element could be provided to produce even broader temperature control. Although it was not analyzed for this case we would expect that adding an indirect evaporative cooling element to these systems would have eliminated the few hours of excursion above the maximum dry bulb temperature.
As a means to dramatically reduce energy consumption for these data modules the evaporative cooling solutions would prove to be extremely effective. Since evaporative cooling systems are also relatively simple mechanical systems with no refrigerants maintenance of the systems does not require licensed refrigeration technicians and there are very few elements that could fail...increasing uptime and providing much faster recovery time should a repair be necessary.